In the use of purified water equipment is the most important point is to ensure the normal operation of the equipment, the normal operation of the equipment to use water to be guaranteed, and the stable operation of the equipment must be inseparable from the usual maintenance and correct use, kerui company to introduce to you the use of purified water equipment to pay attention to what.
1. The device is out of operation
The device cannot be shut down for a long time. If the machine is going to be shut down for more than 72 hours, a chemical cleaning device should be used to charge 1% sodium sulphate and 18% glycerine into the assembly for protection.
Ii. Reverse osmosis device
The reverse osmosis device should be flushed for 10 minutes under the condition of 0.4mpa of water inlet pressure when it is started after each stop.
Use of purified water equipment and effluent quality
Regular detection of purified water equipment use and effluent quality.
Main recording contents shall include: inlet water: pH value, conductivity, pressure, SDI, water temperature;
Water production: conductivity, flow rate, pH value;
Concentrated water: flow rate, pressure and inlet pressure of each section.