Electrical control and cleaning methods of reverse osmosis equipment
Reverse osmosis device is primarily a permeability membrane by means of choosing capability to pressure as the driving force of membrane separation technology, when making use of and when the system pressure is greater than for aqueous solution, osmotic pressure, the water molecules through the membrane, plenty of through production flow into the central tube, and then out in the end the impurities in the water, such as ion, organic matter, bacteria, viruses, etc., trapped on the inlet side of the membrane, and then in the thick water outflow water end, so as to achieve separation and purification.
Electrical control of reverse osmosis equipment
For use in the process of reverse osmosis equipment is mainly used to control the normal operation of the reverse osmosis system, effective here includes dashboard, all kinds of electrical protection, control panel, electric control cabinet, etc.
Cleaning of reverse osmosis equipment
Mainly consists of cleaning water tank, cleaning water pump and precise filter.
When the anti-osmosis system is not satisfied with the water discharge index, the reverse osmosis should be cleaned and restored.
The cleaning method of reverse osmosis equipment
Reverse osmosis technology when use the technology because of its special superiority and increasingly extensive application, reverse osmosis water purification equipment cleaning problems could make many technical strength is not strong user loss, so to reverse osmosis equipment management, can avoid the serious problem.
Low pressure flushing reverse osmosis equipment
Regularly for reverse osmosis equipment of large flow, low pressure, low pH flushing for stripping adhesion on the membrane surface dirt, maintain membrane performance, or when the reverse osmosis device SDI jump more than 5.5, the water should be low pressure flush, again after being qualified SDI value to boot.